Public Record Summary Information of Underground Storage Tanks
The State Water Resources Control Board (State Water Board) has prepared the data below, in compliance with the requirements of the National Energy Policy Act of 2005, summarizing the State of California’s total number of active underground storage tanks (USTs), active UST facilities, the number of UST facilities inspected between July 1, 2020 and June 30, 2021 and the findings from those inspections. Also provided below, is a summary of the source and cause of confirmed unauthorized releases from USTs reported during the same period.
Post Date: November 1, 2021
Summary of Information on Underground Storage Tanks
Data and Inspection Period:
Total Active UST Facilities:
Total Number of Facilities Inspected:
Total Active UST Systems:
Percent of UST Systems in Compliance:
July 1, 2020 – June 30, 2021
*In compliance indicates the UST system has met a series of performance measures developed by and reported to the United States Environmental Protection Agency (U.S. EPA). Other non-reportable violations, such as those not meeting specific state UST regulations, may also be included in the compliance percentage. More information on the U.S. EPA performance measure can be found on their UST Performance Measures web page.
UST Facility, System, Inspection and Compliance Information
The active number of UST facilities, UST systems and corresponding inspection information for this reporting period consists of 13,646 regulated UST facilities, of which 36,073 petroleum UST systems and 1,487 hazardous material UST systems were identified. These numbers, including the percent of USTs in compliance are based on those facilities and UST systems regulated pursuant to Subtitle I in 40 CFR 280.12 (except for tanks identified in 40 CFR 280.10(b) and 280.10(c)), California Health and Safety Code, division 20, chapter 6.7 and California Code of Regulations, title 23, division 3, chapter 16. The percent of UST systems in compliance is further measured using the Federal Technical Compliance Rate (TCR) as clarified by the State Water Board guidance on TCR criteria in LG-164-4. The TCR compliance data collection and reporting began on October 1, 2018 with the implementation of new California UST regulations.
Summary of UST Unauthorized Release Source and Cause (October 1, 2020 – September 30, 2021)
|Spill||Overfill||Physical or Mechanical Damage||Corrosion||Installation Problem||Leak Detection||Other||Unknown||Total|
|Tank||0 (%)||0 (%)||3 (12%)||4 (16%)||0 (%)||0 (%)||0 (%)||18 (72%)||25 (100%)|
|Piping||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||(%)|
|Dispenser||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||1 (100%)||1 (100%)|
|Turbine Sump||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)|
|Delivery Problem||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)|
|Other||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||0 (%)||3(10%)||26 (90%)||29 (100%)|
|Total||0 (%)||0 (%)||3 (6%)||4 (7%)||0 (%)||0 (%)||3 (6%)||45 (81%)||55 (100%)|
* Data shown as number of releases (percent of total)
UST facility and compliance information is prepared biannually by local implementing agencies and collected by the State Water Board March 1 and September 1. This information presented on this page is a portion of the data reported to the U.S EPA. The additional information reported to U.S. EPA can be found at the U.S. EPA Performance Measures web page. For questions regarding compliance data for a specific UST facility, please visit the CalEPA directory for local implementing agency contact information. Unauthorized release source and cause data is collected using State Water Board’s Geotracker. Unauthorized release source and cause data is uploaded to Geotracker by the nine Regional Water Quality Control Boards and by counties approved by the State Water Board as a Local Oversight Program. For unauthorized release source and cause information at a specific location, please visit the Geotracker website.
Red Tag Data
Underground storage tanks determined to have a significant violation that poses an imminent threat to health, safety of the environment may have a red tags affix by the local implementing agency preventing that UST system from either accepting fuel deliveries or dispensing fuel. There are three categories of significant violation:
- A violation causing or threatening to cause a release to the environment
- A violation that impairs the leak detection system
- A chronic violation committed by a recalcitrant violator
Information and data collection for affixed red tag can be found on the State Water Board Red Tag Data and Regulations web page.
For information about this page, please contact Steven Mullery or (916) 341-5508.