Revised Total Coliform Rule
Beginning July 1, 2021, the California Revised Total Coliform Rule (RTCR) will become effective. The revisions include the new Coliform Treatment Technique requirement replacing the Total Coliform MCL, and a new E.coli MCL regulatory limit. The Revised Total Coliform Rule establishes a “find-and-fix” approach for investigating and correcting causes of coliform problems within water distribution systems
Under the headings below, you will find guidance and forms to help comply with the RTCR requirements.
Bacteriological Sample Siting Plans
Existing bacteriological sample siting plans will comply with the new Federal rTCR requirements provided the plans:
- Identify repeat sample locations for each routine sample location
- Identify triggered source sampling needed to comply with the Groundwater Rule
- Identify the sample schedule and rotation plan among sampling sites for collection of routine, repeat and triggered source sampling
If your existing plan does not include the additional requirements above, please submit a new plan to your local regulating agency (DDW District Office or County Environmental Health Office). A sample bacteriological sample siting plan will be available soon.
Routine and Repeat Sampling
Routine sampling frequency and number of required samples remain the same for all water systems. Within 24 hours following a total coliform-positive sample result, water systems shall continue to collect a repeat sample set of 3 samples. All routine and repeat samples must be collected according to the approved bacteriological sample siting plan above.
Level 1 Assessment
|If a water system collects...||Level 1 Assessment is required within 30 days if...|
|...Less than 40 routine and repeat samples per month||More than 1 TC-positive sample in a month|
|...40 or more routine and repeat samples per month||More than 5.0% TC-positive samples in a month|
Under the RTCR, a water system which exceeds the trigger levels in the table above must also conduct a Level 1 Assessment. The completed assessment must be submitted to the local regulating agency (DDW District Office or County Health Office) within 30 days of exceeding the trigger level. The Level 1 Assessment will require water systems to identify a possible cause to the total coliform positive samples and corrective actions taken/needed. Failure to complete the corrective actions will be a violation of the Coliform Treatment Technique in the RTCR.
Templates for the Level 1 Assessment for different types of water systems are available below:
- Level 1 Assessment for simple water systems (well, pressure tank, no treatment/chlorination)
- Level 1 Assessment for most groundwater systems (wells, storage/pressure tanks, chlorination)
- Level 1 Assessment for water systems with a surface water treatment plant
- Level 1 Assessment for groundwater systems with chemical removal treatment
- Level 1 Assessment for transient, non-community water systems
Public notification (Tier 2) will be required within 30 days of the exceedance and a template will be available soon.
E.coli MCL Exceedances / Level 2 Assessment
E.Coli MCL Exceedances
- E.coli-positive repeat sample following TC-positive routine sample
- TC-positive repeat sample following an E.coli positive routine sample
- Failure to collect all required repeat samples following a E.coli-positive routine sample
- Failure to test for E.coli when any repeat sample is TC-positive
Under the RTCR, a water system exceeds the E.coli MCL when any of four trigger levels above are met. In addition, the Federal RTCR adds two new conditions to the E.coli MCL for failing to collect all required repeat samples following a E.coli positive routine sample and failing to test for E.coli after a total coliform positive repeat sample. The water system must notify the local regulating agency (DDW District Office or County Environmental Health Office) by the end of the business day to schedule a Level 2 assessment. Similar to the Level 1 assessment, the Level 2 Assessment will require the water system to identify a possible cause to the total coliform positive samples and corrective actions taken/needed. However, the Level 2 Assessment will be performed by the local regulating agency. Failure to return the assessment or complete the corrective actions will be a violation of the Coliform Treatment Technique in the RTCR.
Public notification (Tier 1) will be required within 24 hours of the exceedance and a template will be available soon.
Seasonal Water Systems
Non-community water systems which do not operate on a year-round basis (e.g. starts-up and shut down at the beginning and end of each operating season) must have an approved, written start-up procedure to comply with the Federal RTCR requirements. Seasonal water systems are required to follow this start-up procedure which includes:
- an inspection of water system components,
- disinfection and flushing,
- coliform and chlorine residual monitoring,
- use of certified distribution operators to perform 1-3 above,
- notification to local regulating agency (DDW District Office or County Environmental Health Office) upon start-up.
Monthly Coliform Reporting
All water systems are required to report results of coliform monitoring monthly by the 10th day of the following month. A revised monthly summary form and instructions are available below.
- Monthly Coliform Reporting Form (available by request)
- Instructions for completing Monthly Coliform Reporting Form (available by request)
- USEPA Revised Total Coliform Rule Information
- Revised Total Coliform Rule Analytical Methods (ELAP webpage)
Regulatory Agency Contact Information
- Division of Drinking Water District Field Office Contact Information
- Local Primacy Agency Contact Information
In February 2017, the State Water Board released a draft of the planned regulation text and held six public workshops throughout California to receive input on the rule. The California version of the RTCR will follow many of the federal requirements, with some exceptions as indicated in the workshops.
- VIDEO: Revised Total Coliform Workshop Presentation in Sacramento - March 29, 2017
- Draft CA Revised Total Coliform Regulations - February 3, 2017
- Revised Total Coliform Rule Workshop Presentation - (PowerPoint)
- RTCR Workshops Public Notice